The Evolution of
A TIMELINE OF HOW FAR FIRESTOPPING HAS COME OVER THE YEARS. By Don Pilz and Brent Johnson
approximately 40 years. This was kick started from the 1980 MGM Grand fire in which 85 people were killed (including seven employees) and 650 injured, including guests, employees, and 14 firefighters. Insurance companies were the driving force behind promoting and developing firestop products to minimize the risk of property lost. This created an increased demand for firestopping which ultimately lead to changes in the building codes. At first, builders used what was readily available for firestopping. Drywall,
mineral wool, steel framing, and spray applied fireproofing were all products already known to restrict the passage of fire. Drywall manufacturers designed wall assemblies that could be tested per design standards found in ASTM E119 and ANSI/UL-263. These original assemblies were great for restricting the passage of fire but did not do as well when it came to restricting the passage of smoke or aiding in protection in the event of seismic activity. Given that seventy-five people died from smoke inhalation and carbon monoxide poisoning in the MGM Grand fire, smoke seals became front and center and out of that came fire sealants and fire sprays (Figure 1). Fire sealants and fire sprays provided an improved flexible joint fill material and a superior smoke seal over the traditional methods of the time.
Although these earlier joint systems offered minimal dynamic movement, recent innovations have led to products such as STI’s SpeedFlex Joint Profile that combines with SpecSeal sprayapplied coatings to provide superior joint movement capabilities in gypsum board construction (Figures 2 & 3).
In 2012, a major code change was adopted into the 2012 International Building Code, “Special Inspections” for firestop penetrations and joints. Special inspections will require visual and or destructive testing. Destructive testing occurs when the special inspector will wait until the firestop product is fully cured and then take a “coupon” (removal of field installed firestop sealant or fire spray) of the sealant/spray to verify its depth at multiple locations at the bond lines. The bond line would be either at the penetration or the perimeter joint of the substrate interface. This code change was the result the firestopping industry wanted to ensure for proper installation of firestopping from qualified installers.
Preformed Fully Cured Firestopping
As with all major code changes, such as the 2012 IBC requirement for “Special Inspections” of firestop penetrations and joints, the firestopping manufacturers looked to develop products that could be easily inspected, easily installed, and reduce potential installation errors. In 2015, preformed/fully cured firestop products were introduced into the market. These products minimized installation error by providing products with factor metered dosage. Being fully cured products, they also provided easier and immediate inspections with no wait time. Today, nearly all the major firestop manufactures offer some type of preformed/fully cured firestopping for joints and penetrations (show in the figures on the following page).
Fire Rated Drywall Accessories
STC (Sound Transmission Class)
While firestopping is critical to modern construction, Sound Transmission Class (or STC) is quickly becoming equally important for overall “quality of life” in residential construction. STC is an integer rating of how well a building partition attenuates airborne sound. The higher the STC number, the better the sound protection. With such an importance on STC ratings, modern day firestopping products will be expected to provide superior STC ratings. This means firestopping products will now have to undergo even more 3rd party testing for sound ratings. The AHJ (Authority Having Jurisdiction) should be mindful of this STC requirement as there are many different firestop products to choose from but they may not provide the suitable 3rd party sound testing reports.
To best prepare for these special inspections and help your project have the most code compliant solution for the total life cycle of the structure, it has never been more imperative to properly select and install per tested listed systems as required in section 715 of the IBC.
As product offerings continue to provide the contractor and design professional more options to meet today’s construction demands, there still are listed systems behind every installation needed for a project to meet your building code requirements and help reduce risk and liability for all parties involved. Additionally, the special inspector will be required to inspect any type of product used per ASTM E2393 and most likely will be required to perform a visual inspection during the time of installation for a preformed or precured firestopping joint product. These new product categories could help reduce some steps of inspection in certain Tested Listed Systems where mineral wool compression calculations or destructive samples of sealant depth may no longer be required. To help limit delays on your project please remember to take all aspects of your design into the selection of these Tested Listed Systems and corresponding products, starting with your wall design, stud depths, designation of barriers (smoke barrier vs. fire barrier), building movement tolerances, STC values, etc. There are currently thousands of systems to select from, which is a huge improvement from the handful that were available in the early stages of the industry. But with that also comes confusion and assumptions that products hold the rating. Many websites, associations and companies are available to help aid you in the firestopping design process starting with the Firestop Manufacturer, Firestop Consultant and Firestop Specialty Contractor.
Fire and Life Safety
As the industry continues to grow and provide projects simpler yet faster materials to improve fire/smoke compartmentalization, it is imperative to remember that proper Firestop Design starts before any dirt is moved on a construction site.
Being more proactive in your Firestop Design and selection of Firestopping Tested Listed Systems during preconstruction can not only help you reduce costs/delays during installation and inspection but also ensure your project is taking all of your buildings’ needs into consideration to meet building code requirements on this imperative and often misunderstood scope of Fire and Life Safety.There are available resources such as the International Firestop Counsel, which is a nonprofit association of manufacturers, distributors, installers, inspectors and other key stakeholders interested in passive fire protection materials and systems in North America and abroad. With over 3 decades of members’ experience and a constant stream of innovation, the IFC is the one-stop source of firestop expertise. The IFC also provides impartial broad-based education, information, procedures regarding firestop system selection, performance, installation and inspection to the construction and code-enforcement communities
— Don Pilz —
With 30-plus years in the construction industry as a foreman
and building Consultant, Don Pilz is now the R&D Manager
for CEMCO assisting consultants, architects and contractors with interior and exterior performance detailing. He can be reached at (626) 506-3881 or email@example.com.
— Brent Johnson —
Brent Johnson is the president of FireWise Consultants and
has been specializing in firestop design and education since
2006. He currently is a member of the International Firestop
Council and FCIA, an Intertek Qualified Firestop Inspector
and leading educator in the country concerning Firestop
Special Inspections. Johnson can be reached at brent@
Original article published in Walls & Ceilings Magazine (link the name of the magazine to this page https://www.wconline.com/articles/92546-the-evolution-of-firestopping ) Republished on July 7, 2020 with permission from Don Pilz.